Thursday, December 17, 2015
Spot “Vs” Area Temperature Measurement using IR Cameras
Over the years I have been involved in the infrared industry I have seen some mistakes made and problems missed using spot temperature measurements on IR cameras, luckily these were rectified using the IR software when the reports were written… (would not have been the case had we been using “report by exception” techniques!).
I have always trained my thermographers to use area measurement at all times, in particular the “area max temperature function” this way we ensure that we do everything to make sure we don’t miss anything that may be detrimental during the inspection, and this is more important when inspecting through IR Windows!
There are instances when the use of spot temperature measurement techniques are very effective, especially when trying to compare one item to another in an IR image to see what the temperature difference is, or when trying to correlate one component to another, etc… However as a rule I have always found it best practice to use the area maximum temperature function whilst conducting electrical surveys using IR cameras.
Design For Safety & Reliability
Designing for Safety & Reliability (DFSR) is focused on protecting workers and operational integrity while creating a ...
Wireless Temperature Monitoring for Critical Asset Management
Continuous monitoring of critical electrical assets enhances an existing condition-based maintenance program and alerts the ...
Related Videos and Articles
The IRISS Ecosystem: A World of Safety & Reliability
The IRISS ecosystem is a full-scope of approach to worker safety, asset reliability, and operational efficiency. Our 3-Step ...
Delta-T Wireless Temperature Monitoring
The Delta T Alert System from IRISS provides you with a quality solution to monitor your assets health and manage their rel ...
Detecting PD & Protecting Critical Assets
Asset reliability is crucial to the continued operations of companies throughout the world. From Data Centers and Manufacturing P ...